Fire Foam Suppression System - Foam is used whenever there is a prospect of a liquid fire. The Foam will mix with water and then develop over the liquid that is on fire, cool the fire, and will finally choke it.
Fire Foam Suppression System is mostly Used in:
Foam Fire Sprinkler Systems offer a recognized technology for the control of burning flammable liquids. Foam fire sprinkler systems operate by mixing a foam concentrate at specific proportions with water to create a foam blanket that overwhelms a fire. The distribution of a foam blanket over a flammable liquid will extinguish a fire by eradicating the fire's oxygen supply and provide a cooling effect on the burning fuel.
Foam concentrate is stored within a tank and can be presented into the sprinkler water through several different methods. A bladder tank which is the simplest form of storage will use a proportioned to introduce and mix the foam concentrate with the sprinkler water. Foam concentrate is forced from the tank by introducing water around a bladder which "squeezes" foam from the tank and forces it into the proportioner. The operation of a bladder tank system is completely mechanical; it does not require the use of electrical components which could fail as a result of a fire. Another means of foam concentrate delivery is through the use of a foam pump. This pump takes supply of foam from a storage tank and pumps foam into the sprinkler system at a required percent concentration. The foam pump system will operate over a variety of sprinkler system flows and when the hazard is at a greater distance from the foam storage location.